Setpoints are what allow you to set how your equipment responds to its demands and what those demands will be. Almost every equipment on your system will have some set points to calibrate. It is possible to have stand alone equipment that controls itself. These equipments will have monitor only points.
Image 1-1 | History chart builder tool.
To find the setpoint page for the desired equipment got to the mobile navigation page by pressing the Nav button at the top of the screen (image 1-1). Once you are there press the button for the desired equipment. This will load that equipments points and setpoint page(image 1-2).
The equipment page will have various points that can be view by scrolling in top section of the equipment. Below this is a septate scrolling pane for the setpoints, Alarm Limit setpoint, and notes.
Image 1-2 | Mobile Email Configuration.
A setpoint controller has two displays fields and three buttons titled override, auto, and set (image 2-1). The fields display the name of the setpoint and its current value.
Image 2-1 | Setpoint display and control.
Override: When the override button is pressed a pop-up window will appear. There are two fields in which you can edit; Override Value and Override Duration. The Override Value field is where you enter your desired setting. The override Duration pull-down menu allows you to set the length of time the Override Value will last. When a point is overridden it will the display fields color to purple (image 2-2).
Image 2-2 | Overridden setpoint display.
AUTO: This button is used to disable an overridden point and have it resume at its normal setting.
SET: Pressing this button causes a pop-up window to appear that allows you to change the setting value of that point.NOTE:
If a point is overridden using the Set button will have no effect until the overridden value duration ends or the auto button is pressed.NOTE:
The purpose of the override feature is to make quick or temporary changes to the system. If you override a value and set the duration to be permanent it would be recommended to use the set button instead of override.
The space temperature alarm limit setpoint (image 3-1) option allows you to configure if or when and alarm email is sent out to (To learn about Email Notification click here). To enable the alarm the box must be checked. Doings so enables the field. This field can be used to set the limit that must be reached before an alarm is created. The high limit watches for the temperature to rise above the value while the low limit alarm watches for the temperature to drop below the value. In either case an alarm will be generated and email will be sent out if the email notification is set up.
Image 3-1 | Space temp alarm limit configuration.NOTE:
As with all filed editing, the save button must be pressed to make any changes effective. This includes the check boxes.
This section allows for custom notes to be made for the users benefit. For example a list of emails could be saved here for quick copy and paste. As with any field editing, the save button must be pressed to save any entered data or changes. See image 4-1.
Image 4-1 | Notes field.
Still need help? You can visit our contact us page by clicking here.